- Project Name
- Davie Hall 1st floor Air Handler Replacements
- Type of Services
- Project Manager
- Joe Ockert
- Phone Number
- Contact Email
- Closing Date
- Project Budget
Davie Hall was built in 1908 and the addition added in 1967. It is used by the Department of Psychology and Neuroscience.
The air handlers for this building are located in the lower mechanical room and are mostly original units. This project
will replace the original AHU 1A, 1B and 1C. Unit 1A is a 20% outside air multi-zone unit rated for 11,550 CFM and 34
Tons of cooling, Unit 1B is a 100% outside air multi-zoneunit rated for 3,214 CFM and 20 Tons of cooling and Unit 1C
is a 100% outside air multi-zone unit rated for 4,285 CFM and 23 Tons of cooling. Units 1A & 1B condition air used in the 1st floor West offices & clinical labs and Unit 1C conditions air used in the 1st floor East classrooms and clinical labs. The AHU's are in poor condition and have condensate leaking from the housings, air leakage from the doors and module joints, interior corrosion, and the pneumatic controls are worn. The new air handler will be digitally controlled with a variable speed fan drive, and new zone reheat coils will be installed.
Advertisement Type: Designer Solicitations